Fuel gas heating is used for several applications. Besides fuel gas heating to increase gas turbine performance, many of the applications are related to the dewpoint of the gas.
For these applications Eltacon Engineering uses several techniques, like shell and tube heating or electrical heating, based upon the available utilities at site and feasibility.
In order to guarantee the fuel gas used for gas turbines and gas engines is dry for combustion, a heater can be used to superheat the gas to a required temperature above the dewpoint of the gas (water and hydrocarbon dewpoints considered).
A common set-up for a gas treatment unit is a combination of a coalescer filter system with downstream superheating.
Joule Thomson heaters
Using pressure reduction stations in fuel gas treatment runs will cause the fuel gas to cool down due to the Joule Thomson effect. Depending on the dewpoint of the gas, re-heating of the gas might be necessary to avoid condensation downstream the reduction section. The heater can be set to maintain the inlet temperature of the system, or used as a dewpoint heater with a pre-set fuel gas outlet temperature.
One technique utilized to enhance combined cycle power plant performance is to heat the gas turbine fuel gas. Heat is extracted mostly using the cooling water of the gas turbine and is used to raise the temperature of the fuel yielding an improvement in net plant heat rate.
The availability of the heater and performance will depend on the available utility and is therefore not to be used as dewpoint heaters.
Eltacon Engineering BV. uses electrical heat bundles to superheat the gas. These bundles are fed by a Thyristor Control Unit, included in the delivery.
Shell and Tube heaters
Mainly used for performance heating, the shell and tube heaters will be used to heat the fuel gas by using hot water, steam or oil depending on the available utilities. Outlet temperature control is included in the unit control panel or can be integrated in the DCS.
In order to avoid the necessary additional safety equipment (auxiliary equipment to safeguard pressure leakage), a safety heat exchanger can be installed using double tube technology.